We design and manufacture industry-leading hydronic products and solutions that give you control at every turn and help create energy-saving, cost-efficient HVAC installations.
Ensuring you have control at every turn is what we’re all about. We’ve developed a range of applications and software downloads to help you design, install and optimize every type of HVAC solution.
Download library We’ve created an extensive library of product-related technical documentation and a wide range of other useful information to help you get the most out of our globally-renowned products and solutions.
Fully customisable by smartphone via Bluetooth using a TA-Dongle.
More than 200 setup options allow input and output signals, binary input, relay, characteristics and many other parameters to be configured.
Tracks the last 10 errors to allow system faults to be found quickly.
Identical settings can be quickly copied from TA-Dongle to several TA-Slider actuators.
Proportional controlManual overrideStroke detectionMode, status and position indicationStroke limitation settingValve blockage protectionValve clogging detectionError safe positionDiagnostic/LoggingBACnet/Modbus version:+ 1 binary input, max. 100 Ω, cable max. 32.8 ft or shielded.+ 1 connection for Pt1000 temperature probe.BACnet/Modbus CO (change-over) version:+ 1 binary input, max. 100 Ω, cable max. 32.8 ft or shielded.+ 2 connections for Pt1000 temperature probe.+ 1 relay, internally wired for control of TA-M106 actuator on TA-6-way valve (max. 2A, 30 VAC/VDC on resistive load).
24 VAC/VDC ±15%.Frequency 50/60 Hz ±3 Hz.BACnet/Modbus CO:24 VAC only for enabling powering of TA-M106 actuator.
BACnet/Modbus:Operation: < 1.5 VA (VAC); < 1.0 W (VDC)Standby: < 1.2 VA (VAC); < 0.75 W (VDC)BACnet/Modbus CO:Operation: < 1.5 VA (VAC)Standby: < 1.2 VA (VAC)TA-M106 actuator consumption must be added separately.
By BACnet/Modbus or with hybrid control mode;0(2)-10 VDC, Ri 47 kΩ.Adjustable hysteresis sensitivity 0.1-0.5 VDC.0.33 Hz low pass filter.Proportional:0-10, 10-0, 2-10 or 10-2 VDC.Proportional split-range:0-5, 5-0, 5-10 or 10-5 VDC.0-4.5, 4.5-0, 5.5-10 or 10-5.5 VDC.2-6, 6-2, 6-10 or 10-6 VDC.Proportional dual-range (for change-over):0-3.3 / 6.7-10 VDC,2-4.7 / 7.3-10 VDC,0-4.5 / 5.5-10 VDC or2-5.5 / 6.5-10 VDC.Default setting: By BACnet/Modbus. If Hybrid mode chosen, default input signal is Proportional 0-10 VDC.
Linear, EQM 0.25 and inverted EQM 0.25.Default setting: Linear.
254 s/in (10 s/mm)
36/45 lbf (160/200 N)
Self-adjusting for IMI Hydronic Engineering valves.
Media temperature: max. 248°FOperating environment: 32°F to 122°F (5-95%RH, non-condensing)Storage environment: -4°F to 158°F (5-95%RH, non-condensing)
(according to EN 60529)
(according to EN 61140)
Separate overmoulded cables (see Additional equipment).Type LiYCY 5x22 AWG (5x0.34 mm2) (cables A and B) and type LiYY 6x22 AWG (6x0.34 mm2) (cable C).Halogen free, fire class B2ca – s1a, d1, a1 according to EN 50575.Relay cable (CO version): Type LiYY 3x22 AWG (3x0.34 mm2).3.28 ft, 6.56 ft or 16.4 ft. With connector to actuator TA-M106.Halogen free, fire class B2ca – s1a, d1, a1 according to EN 50575.
0.27 in (6.9 mm)
Automatic detection of the valve lift (stroke detection).
Max. 30 dBA
BACnet/Modbus: 0.48 lbBACnet/Modbus CO: 0.57 lb, 3.28 ft relay cable 0.68 lb, 6.56 ft relay cable0.99 lb, 16.4 ft relay cable
Retainer nut M30x1.5.
Cover: PC/ABS GF8Housing: PA GF40.Swivelling nut: Nickel-plated brass.
White RAL 9016, grey RAL 7047.
Label: IMI TA, CE, product name, article No. and technical specification.
LV-D. 2014/35/EU: EN 60730-1, -2-14.EMC-D. 2014/30/EU: EN 60730-1, -2-14.RoHS-D. 2011/65/EU: EN 50581.
Articles - TA-Slider 160 BACnet/Modbus
TA-Slider 160 BACnet/Modbus
Digitally configurable actuators for Bus communication with BACnet MS/TP or Modbus RTU, with or without change-over. A wide range of setup options provide extensive flexibility for on-site parameter adaptation. Fully programmable binary input, relay and adjustable max. stroke of the valve bring new opportunities for advanced hydronic control and balancing.
Input signal: Via Bus or 0(2)-10 VDC
Articles - TA-Slider 160 BACnet/Modbus CO
A: To connect the first TA-Slider 160/500 BACnet or Modbus of a daisy chain to the Bus.B: Between two actuators in a daisy chain.C: To enable hybrid mode or provide power supply if the daisy chain is long.
For Bluetooth communication with the HyTune app, transfer configuration settings and manual override.