Domestic hot water systems.
Control of domestic hot water supply or of similar smaller systems.
Max. dynamic pressure: 500 kPa
Max. inlet pressure ratio (H/C or C/H): 2:1
Max. working temperature: 90°C
Min. ∆t between inlets and outlet: 10°C
Temperature can be adjusted between 35-60°C
Factory temperature setting: 35°C
Water or neutral fluids, water-glycol mixtures (0-50%).
Valve body: Brass CW625N, UNI EN 12165.
Inner parts: PSU and ULTEM.
Springs: Stainless steel.
Internal seals: EPDM.
Thermostatic element: Wax
IMI TA, TA-Mix, PN, DN, CR, C - H - MIX.
External threaded couplings.
Threads according to ISO 228.